Name of person filing report: Sergii Iakymov
Reason for Report: Routine
Non-Nominal Systems: A tunnel stick on the right from the rear airlock. Director’s trailer heater.
SOC Last 24 hours: Max 100%; Min 63%; Avg 74.5%.
VDC Last 24 hours: Max 59.01V; Min 43.63V; Avg 48.61V.
Generator run time: 4048.8 hours.
Station Tank: 70%
Director Tank: 70%
Intern Tank: 71%
Generator Tank: 51%
Hab Static Tank – 275.5 gallons
GreenHab – 171 gallons
Outpost tank – 430 gallons
Science Dome – 0 gallons
Hab Toilet Tank emptied: No
Sojourner rover used: Yes, around the station.
Beginning Charge: 100 %
Ending Charge: 100 %
Currently Charging: Yes
Notes on Rovers: All rovers serviced and damaged fuse terminals replaced. All EVA rovers got equipped with rear view mirrors.
ATV: ATV’s Used: None. Nothing to report.
Hab Car used and why, where: To Hanksville for supplies. Need to be serviced.
Crew Car used and why, where: To Hanksville for supplies.
General notes and comments: All cars awaiting renewed insurance ID.
Summary of Internet: All nominal.
EVA suits and radios:
Suits: All nominal
Comms: All nominal
Campus wide inspection, if action taken, what and why: One tunnel stick on the right from the rear airlock is corroded out at the ground level and needs to be replaced. Repair is scheduled to be done by the end of next week.
Summary of Hab Operations: Nothing to report
Summary of GreenHab Operations: All nominal
Summary of SciDome Operations: All nominal
Summary of Observatories Operations: All nominal.
Summary of RAM Operations: All nominal.
Summary of Outpost Operations: Director’s trailer heater is non operational. New heater will be ordered next week.
Summary of Health and Safety Issues: All nominal.